Sunday, 1 January 2012
Contactors and Motor starters
Most motor applications require the use of remote control devices to start and stop the motor. Magnetic contactors, similar to the ones shown below, are commonly used to provide this function. Contactors are also used to control distribution of power in lighting and heating circuits.
Basic Contactor Operation
Magnetic contactors operate utilizing electromagnetic principles. A simple electromagnet can be fashioned by winding a wire around a soft iron core. When a DC voltage is applied to the wire, the iron becomes magnetic. When the DC voltage is removed from the wire, the iron returns to its nonmagnetic state. This principle is used to operate magnetic contactors.
The following illustration shows the interior of a basic contactor. There are two circuits involved in the operation of a contactor. The control circuit and the power circuit. The control circuit is connected to the coil of an electromagnet, and the power circuit is connected to the stationary contacts.
The operation of this electromagnet is similar to the operation of the electromagnet we made by wrapping wire around a soft iron core. When power is supplied to the coil from the control circuit, a magnetic field is produced magnetizing the electromagnet. The magnetic field attracts the armature to the magnet, which in turn closes the contacts. With the contacts closed, current flows through the power circuit from the line to the load. When the electromagnet’s coil is de-energized, the magnetic field collapses and the movable contacts open under spring pressure. Current no longer flows through the power circuit.
The following schematic shows the electromagnetic coil of a contactor connected to the control circuit through a switch (SW1). The contacts of the contactor are connected in the power circuit to the AC line and a three-phase motor. When SW1 is closed, the electromagnetic coil is energized, closing the “M” contacts and applying power to the motor. Opening SW1 de energizes the coil and the “M” contacts open, removing power from the motor.
Contactors are used to control power in a variety of applications. When applied in motor-control applications, contactors can only start and stop motors. Contactors cannot sense when the motor is being loaded beyond its rated conditions. They provide no overload protection. Most motor applications require overload protection. However, some smaller-rated motors have overload protection built into the motor (such as a household garbage disposal). Overload relays, similar to the one shown below, provide this protection. The operating principle, using heaters and bimetal strips, is similar to the overloads discussed previously.
Contactors and overload relays are separate control devices. When a contactor is combined with an overload relay, it is called a motor starter.
Motor Starter in a Control Circuit
The following diagram shows the electrical relationship of the contactor and overload relay. The contactor, highlighted with the darker grey, includes the electromagnetic coil, the main motor contacts, and the auxiliary contacts. The overload relay, highlighted by the lighter grey, includes the “OL” heaters and overload contacts. The contactor and the overload relay have additional contacts, referred to as auxiliary contacts, for use inthe control circuit. In this circuit a normally closed “OL” contact has been placed in series with the “M” contactor coil and L2. A normally open “M” auxiliary contact (“Ma”) has been placed in parallel with the “Start” pushbutton.
Contactors and Motor starters
Basic operation of Contactors and Starters|Circuit diagram of motor starter|Motor starter in control circuit|overload relay operation|
PLC Ladder PLC Practice Problem PLC Ladder Programming training & tutorials Free Training on PLC Ladder Programming training & tutorials PLC Ladder Logic PLC Timer SCADA Basic PLC Ladder Programming Examples Delta PLC PLC & Visual Basic Communication PLC Definition Introduction PLC Error PLC Error LED RSLinx Tutorial Types of Timers in PLC ladder logic Programming programmable Logic Controllers AB addressing ABB AC Drive AC Drive training cource Actuators Advantages and Disadvantages Addressing of Allen Bradley PLC Micrologix 1000 Addressing of Delta PLC DVP SS/ES/EX Addressing of Mitsubishi PLC FX2N Addressing of Modicon PLC Micro TSX 3722 Addressing of Siemens PLC S7 200 Advantages & Disadvantages of RTD Advantages & Disadvantages of all types Sensors Advantages of SCADA Allen Bradley PLC PWM (Pulse Width Modulation) error codes Allen Bradley SLC Controller Error Codes Ampere Voltage Ratings of circuit brakers Analog addressing Allen bradley Analog input in Allen Bradley PLC Applications of Sensors Capacitive Proximity Sensors blck diagram Capacitive proximity sensors Circuit brakers Circuit diagram of motor starter Communication Between two E1000 HMI and mitsubishi Fx2n PLC Communication between FX3U PLC and SCADA via RS485BD Configuring the DF1 Driver using RSLinx Configuring the Ethernet Driver Connection between 2 E-Terminals and FX2N PLC. DOL Motor Starter PLC logic DOP Series Human Machine Interface DVP14ss Delta HMI Delta HMI Program Download.Delta HMI Communication Cable Delta HMI and RS485 Communication Delta MMI Delta PLC Projects Delta PLC input output addressing Different types of Special motor Diffrence between PLC and DCS Ebook on Basics of Allen Bradley PLC pdf Ebook on Basics of Siemens PLC pdf Ebook on Basics of VFD PDF download Electrical maintenannce tips Electromagnetic relay Error Messages from RSLogix Emulate 500 Failsafe meaning Features of Delta HMI/MMI Following are the Free PLC Software's available from all leading brands such as Allen Bradley Free PLC Ebooks Free PLC SCADA TRAINNING & TUTORIAL Free PLC Training Full form of HART HART OSI reference model HART protocol structure HMI & ZIGBEE How Capacitive Proximity Sensors Works? How Inductive Proximity Sensor Works? How Ultrasonic Sensors Works? How to Select a Suitable Motor How to Select the Right VFD (Inverter) or AC Motor Drive Ladder Logic for AND Ladder Program for Automatic Door open close Ladder Programs for Gates List of Top Most Widely used PLC’s in the Industry List of Widley used PLC Companies. Low cost Wireless I/O’s using PLC Mitsubishi Mitsubishi PLC FX2N & HMI E1000 Networking using BDTP Technology Mitsubishi PLC input output addressing Modbus Communication Modbus Ethernet Modbus Serial Modbus.dll for Visual Basic Mormally open Contact Normally Close Contact Explained Motion Actuators Motor starter in control circuit NAND NO NC Explained NOR Gates with Truth Tables Nashik Nexgenie PLC Features Nexgenie PLC Port Nexgenie PLC input output OFF Delay Timer OLE for Process and Control ON Delay Timer OR Omron On line Ladder Program Editing for RSLogix 500 On line Ladder changes Online Editing Ladder Program Online Servo tuning PID Control Instruction PID PLC PID instruction in Allen Bradley PLC PLC & VB PLC Counter PLC Error Allen Bradley PLC Error messages in Allen Bradley PLC FBD PLC Fault PLC Industrial Automation Training Institute PLC ON Delay Timer PLC Run Led PLC SCADA Communication PLC SCADA DCS Training Centers PLC SCADA Driver PLC SCADA Training Chennai PLC and ZIGBEE PLC application PLC based Automated Guided Vehicle PLC based Final year Project PLC based Line follower robot PLC based Project Report PLC functional Block Diagram PLC input wiring PLC interview Question PLC interview questions PLC maiintence PLC power LED PLC program for star delta starter PLC retentive timer PLC training in Delhi PLC training in Mumbai PLC training in Pune PTO Allen Bradley PTO [Pulse Train Output] Instruction in Allen Bradley PLC Photoelectric Sensor Applications Photoelectric Sensor Applications in Automation industry Power cable Selection Proficy HMI/SCADA Cimplicity 8.1 Programming Languages for PLC Proximity sensor application Push to ON PUSH to OFF PLC program using NO NC and Coil Pwm RSLinx Tutorial | Configuring the DF1 Driver RSLinx Tutorial | Configuring the Ethernet Driver Scaling Analog Input using SCL Instruction in PLC [Scale Data] Schneider Schneider PLC addressing Selction of Servo Motor Selction of Stepper Motor Selection of AC Motor Selection of VFD Selection of stepper or Servo Motor Sensor applications Servo Motor Servo auto tuning Parameters Siemens Siemens input output addressing Signal Cables selection Simatic Wincc SCADA Single Push button to on and off motor Sinking and sourcing operations Softwares used in SCADA Solid State Relay construction Solid State Relay uses and Advantages Sourcing and Sinking Concept in PLC Standard Wiring Color Codes Stepper Motor Applications and Advantages Disadvantages Stepper application Stepper motor Selection Stepper motor and PLC Tag in SCADA Temperature sensors used with PLC Theory of Capacitive Proximity Sensors Theory of Ultrasonic Sensors Theory or Operation of Inductive Proximity Sensors Thermistor & Temp IC Sensors Thermocouple Trial Run of PLC Troubleshooting Allen Bradley PLC with RSLogix Emulate 500 Troubleshooting Tips for Electrical /Electronic Maintenance Tutorial on PLC Types of Actuators Types of Actuators used for Motion in Automation with Advantages & Disadvantages Types of Sensors Types of Timers in PLC | ON Delay Timer (TON) Typical circuit diagram of Star Delta starter Ultrasonic Sensor Applications Ultrasonic sensors Unitronics VB 6.0 and PLC VIsual Basic as SCADA What is HART What is SCADA (Supervisory Control And Data Acquisition) What is SMART Communication What is a PLC ? What is DCS? What is the difference between PLC and Microcontroller? XIO [Examine if Open] & XIC [Examine if Closed] Explained advantages & disadvantages of Servo Motors anlog input addressing DELTA PLC anlog input addressing Mitsubishi PLC anlog input addressing siemens automation training comparison of PLC and DCS connecting field devices to Programmable Logic Controllers contact reting of relay design of fail safe systems digital common ground connections distributed control system drawbacks of Servo Motor fail safe PLC Redundancy modbus examples noise in cables one input one output PLC program using NO NC logic opc overload relay operation photoelectric plc Response Time plc output wiring plc program for TV remote plc training programmable Logic Controllers List relay coil rating relay driving circuit relay isolation voltage selection of relay servo basics servo training star delta starter control wiring diagram types of Counter typical circuit diagram of Direct on line starter