Thursday, 9 February 2012
CABLE Types & Selection
Use wise, the selection of cable can be divided into two categories as follows
1) Power cables
2) Signal cables
The power cables main characteristics required for selection can be listed as
1) High current carrying capacity
2) High line voltages (24 to 220 V dc and 230 V, 415 V to about voltages in kV for ac.)
3) Normally, low and fixed operating frequency like 50 Hz or 400 Hz. The conductors are copper and aluminum. Aluminum cables are used in house wiring for saving cost. However due to low ductility while bending, it develops cracks and hence it is not a preferred material. Aluminum bus bars are used as conductors inside panels.
The three main parameters for selection are
1) Line voltage
2) Line current
3) Line drop from source to equipment
According to Indian standards for voltage less than 415 V ac, the insulation rating of the cable is 1.1 kV. Beyond this, the test voltage is 2 *rated voltage + 1.0 kV.
The manufacturer specifies the maximum current capacity of the cable and this depends upon number of cores, insulation used, type of cooling (the cables used in air have less rating than when used underground). This rating is much less than its fusing current. When the conductor cross-section of the cables is the same, multi strand cable rating is higher than single core cable. This is due to skin effect in single strand cable. Normally the cables current are much below this rating because of the voltage drop consideration across the line and these form the main consideration in its selection. For example, the drop expected between the neutral cable used in single-phase supply, and the power ground wire should not exceed about 3 Volts. While supplying three phase 415 V ac, 50 Hz supply the cable used is three and half. Half specifies that the ground cable size used has half the cross section that of phase. The manufacturer specifies the resistance/ km for the cable. The power cables sometimes are armored for protecting it from mechanical damage and gives added strength to the wire.
The termination of these cables is normally on bus bars through lugs crimped on the cable and lug is fixed on bus bar by nut bolt. The colors of wires are red, yellow, blue and black (black for neutral). For control power wiring 1, 1.5, 2.5 square mm wire of 1.1 kV is used. Gray color is the preferred color.
The main characteristics can be listed as low voltage, low current. The frequency can be from dc to MHz. Frequency is one major parameter in selection of signal cable. It is necessary to match the characteristic impedance of the cable with that of source. The receiving equipment also should have same terminating input impedance. For low frequency, twisted cables are used. The twisted pair helps in reducing the magnetic and RF pickup. For high frequency, coaxial cables are used. The use of these cables reduces capacitance between the two signal carrying wires. Shielded cables are used for RF signals and for signals with high output impedance, for example, pH electrode-probes and oscilloscopes.
INHERENT NOISE IN CIRCUITS
There are two types of noise. One is external interference and the second is the inherent noise of the circuit itself. Inherent noise cannot be eliminated because it is caused by components in the actual circuit, such as resistors within the circuit. The best that can be done is to minimize the noise in a specific bandwidth of interest. The inherent noise in the circuit can be divided into four types of noise commonly encountered as
1) Popcorn noise 3) Schottky (shot) noise
2) Flicker (1/f) noise 4) Johnson noise
Popcorn noise is so called because when played through audio system it sounds like cooking popcorn. It consists of random step changes of offset voltage that takes place at random intervals in the 10+ ms timeframe. Such noise results from high level of contamination and crystal lattice dislocation at the surface of the silicon chip, which results from poor processing techniques and poor quality of material. Today because of proper manufacturing techniques this problem has reduced substantially.
FLICKER (1/f) NOISE
This noise is dominant at low frequencies. It has a power spectral density that is inversely proportional to frequency (hence the term 1/f noise). The noise voltage spectral density is therefore inversely proportional to the square root of the frequency. The noise spectral density drops at 10 dB/decade with rising frequency. Noise with such a spectrum is called “pink” noise. Today it is rarely significant above 50 Hz and in special amplifiers it is below 2 Hz (as in OP-27)
Thermal excitation of the electrons in the conductor cause random movement of the charge. In a resistance, this random current causes a noise voltage, known as Johnson noise, whose amplitude is given by the formula
En =Ö 4k*T*R*B
Where k = Boltzmann constant
T = temperature °K
R = resistance in ohms
B = bandwidth in Hz
Reduction in temperature is not a practical solution because at liquid nitrogen temperature it will reduce by 42%. Reducing the value of the resistors and bandwidth to a minimum are the real solutions. These are more important when the input signal value is small. For example, in audio amplifiers.
The bandwidth of an amplifier is 15kHz..The input resistance is 1k ohm. The source voltage is 1mV and source output impedance is 1k ohm. The temperature is 20° C. The Boltzmann constant is 1.38 *10-23 J/K. Calculate the thermal noise generated by the source. Calculate the input noise power and the input SNR.
En =Ö 4k*T*R*B T=20 + 273=293°K
Current in a conductor consists of a flow of electrons, each of which has a discreet charge. Current in a semiconductor consists of a flow of electrons or holes. The statistical variation in the rate of electron flow results in this noise. This noise is significant only when the bandwidth is large.
SIGNAL TO NOISE RATIO (SNR OR S/N)
Signal to noise ratio is a method that compares the relative (power) magnitude of the two at the frequency of interest. It is indicated in decibels.
SNR = 10 * log10 (S/N) in dB
For example, the signal input power to an amplifier is 3mW and noise is 30mW. The SNR is 20 dB. See the table in EMC notes for acceptable ratio for various circuits.
CABLE Types & Selection
Cable selection|noise in cables|Power cable Selection|Signal Cables selection|
PLC Ladder PLC Practice Problem PLC Ladder Programming training & tutorials Free Training on PLC Ladder Programming training & tutorials PLC Ladder Logic PLC Timer SCADA Basic PLC Ladder Programming Examples Delta PLC PLC & Visual Basic Communication PLC Definition Introduction PLC Error PLC Error LED RSLinx Tutorial Types of Timers in PLC ladder logic Programming programmable Logic Controllers AB addressing ABB AC Drive AC Drive training cource Actuators Advantages and Disadvantages Addressing of Allen Bradley PLC Micrologix 1000 Addressing of Delta PLC DVP SS/ES/EX Addressing of Mitsubishi PLC FX2N Addressing of Modicon PLC Micro TSX 3722 Addressing of Siemens PLC S7 200 Advantages & Disadvantages of RTD Advantages & Disadvantages of all types Sensors Advantages of SCADA Allen Bradley PLC PWM (Pulse Width Modulation) error codes Allen Bradley SLC Controller Error Codes Ampere Voltage Ratings of circuit brakers Analog addressing Allen bradley Analog input in Allen Bradley PLC Applications of Sensors Capacitive Proximity Sensors blck diagram Capacitive proximity sensors Circuit brakers Circuit diagram of motor starter Communication Between two E1000 HMI and mitsubishi Fx2n PLC Communication between FX3U PLC and SCADA via RS485BD Configuring the DF1 Driver using RSLinx Configuring the Ethernet Driver Connection between 2 E-Terminals and FX2N PLC. DOL Motor Starter PLC logic DOP Series Human Machine Interface DVP14ss Delta HMI Delta HMI Program Download.Delta HMI Communication Cable Delta HMI and RS485 Communication Delta MMI Delta PLC Projects Delta PLC input output addressing Different types of Special motor Diffrence between PLC and DCS Ebook on Basics of Allen Bradley PLC pdf Ebook on Basics of Siemens PLC pdf Ebook on Basics of VFD PDF download Electrical maintenannce tips Electromagnetic relay Error Messages from RSLogix Emulate 500 Failsafe meaning Features of Delta HMI/MMI Following are the Free PLC Software's available from all leading brands such as Allen Bradley Free PLC Ebooks Free PLC SCADA TRAINNING & TUTORIAL Free PLC Training Full form of HART HART OSI reference model HART protocol structure HMI & ZIGBEE How Capacitive Proximity Sensors Works? How Inductive Proximity Sensor Works? How Ultrasonic Sensors Works? How to Select a Suitable Motor How to Select the Right VFD (Inverter) or AC Motor Drive Ladder Logic for AND Ladder Program for Automatic Door open close Ladder Programs for Gates List of Top Most Widely used PLC’s in the Industry List of Widley used PLC Companies. Low cost Wireless I/O’s using PLC Mitsubishi Mitsubishi PLC FX2N & HMI E1000 Networking using BDTP Technology Mitsubishi PLC input output addressing Modbus Communication Modbus Ethernet Modbus Serial Modbus.dll for Visual Basic Mormally open Contact Normally Close Contact Explained Motion Actuators Motor starter in control circuit NAND NO NC Explained NOR Gates with Truth Tables Nashik Nexgenie PLC Features Nexgenie PLC Port Nexgenie PLC input output OFF Delay Timer OLE for Process and Control ON Delay Timer OR Omron On line Ladder Program Editing for RSLogix 500 On line Ladder changes Online Editing Ladder Program Online Servo tuning PID Control Instruction PID PLC PID instruction in Allen Bradley PLC PLC & VB PLC Counter PLC Error Allen Bradley PLC Error messages in Allen Bradley PLC FBD PLC Fault PLC Industrial Automation Training Institute PLC ON Delay Timer PLC Run Led PLC SCADA Communication PLC SCADA DCS Training Centers PLC SCADA Driver PLC SCADA Training Chennai PLC and ZIGBEE PLC application PLC based Automated Guided Vehicle PLC based Final year Project PLC based Line follower robot PLC based Project Report PLC functional Block Diagram PLC input wiring PLC interview Question PLC interview questions PLC maiintence PLC power LED PLC program for star delta starter PLC retentive timer PLC training in Delhi PLC training in Mumbai PLC training in Pune PTO Allen Bradley PTO [Pulse Train Output] Instruction in Allen Bradley PLC Photoelectric Sensor Applications Photoelectric Sensor Applications in Automation industry Power cable Selection Proficy HMI/SCADA Cimplicity 8.1 Programming Languages for PLC Proximity sensor application Push to ON PUSH to OFF PLC program using NO NC and Coil Pwm RSLinx Tutorial | Configuring the DF1 Driver RSLinx Tutorial | Configuring the Ethernet Driver Scaling Analog Input using SCL Instruction in PLC [Scale Data] Schneider Schneider PLC addressing Selction of Servo Motor Selction of Stepper Motor Selection of AC Motor Selection of VFD Selection of stepper or Servo Motor Sensor applications Servo Motor Servo auto tuning Parameters Siemens Siemens input output addressing Signal Cables selection Simatic Wincc SCADA Single Push button to on and off motor Sinking and sourcing operations Softwares used in SCADA Solid State Relay construction Solid State Relay uses and Advantages Sourcing and Sinking Concept in PLC Standard Wiring Color Codes Stepper Motor Applications and Advantages Disadvantages Stepper application Stepper motor Selection Stepper motor and PLC Tag in SCADA Temperature sensors used with PLC Theory of Capacitive Proximity Sensors Theory of Ultrasonic Sensors Theory or Operation of Inductive Proximity Sensors Thermistor & Temp IC Sensors Thermocouple Trial Run of PLC Troubleshooting Allen Bradley PLC with RSLogix Emulate 500 Troubleshooting Tips for Electrical /Electronic Maintenance Tutorial on PLC Types of Actuators Types of Actuators used for Motion in Automation with Advantages & Disadvantages Types of Sensors Types of Timers in PLC | ON Delay Timer (TON) Typical circuit diagram of Star Delta starter Ultrasonic Sensor Applications Ultrasonic sensors Unitronics VB 6.0 and PLC VIsual Basic as SCADA What is HART What is SCADA (Supervisory Control And Data Acquisition) What is SMART Communication What is a PLC ? What is DCS? What is the difference between PLC and Microcontroller? XIO [Examine if Open] & XIC [Examine if Closed] Explained advantages & disadvantages of Servo Motors anlog input addressing DELTA PLC anlog input addressing Mitsubishi PLC anlog input addressing siemens automation training comparison of PLC and DCS connecting field devices to Programmable Logic Controllers contact reting of relay design of fail safe systems digital common ground connections distributed control system drawbacks of Servo Motor fail safe PLC Redundancy modbus examples noise in cables one input one output PLC program using NO NC logic opc overload relay operation photoelectric plc Response Time plc output wiring plc program for TV remote plc training programmable Logic Controllers List relay coil rating relay driving circuit relay isolation voltage selection of relay servo basics servo training star delta starter control wiring diagram types of Counter typical circuit diagram of Direct on line starter