Tuesday, 5 May 2015
Types of Timers in PLC | OFF Delay Timer (TOF)
PLC Timers are generally used for delaying an event from taking place, or to delay a device from shutting off either on an on transition or an off transition. There are three types of PLC timers: The Timer ON delay (TON), Timer Off delay (TOF), and the Retentative Timer On delay (RTO).
By default, timers are stored in the T4 Data file, however other time files can be created. A timer consists of the following components: Preset word (PRE), Accumulate word (ACC), Done bit (DN), Timer Timing bit (TT), and Enable bit (EN). For Timers, the Enable bit follows the rung condition.
The entire timer is addressed by it's element (example: T4:0) Pieces of the timer can be used in logic however such as the DN bit on an XIC (T4:0/DN), or the Accumulated value in a MOV statement (T4:0.ACC)
The Off Delay Timer is generally used to delay an event from shutting off. Image a lube system on a large motor. As long as the main motor is turning, the lube pump should be running. When the main motor shuts off, you wouldn't want to shut off the lube pump immediately because the main motor needs time to coast down to zero RPM's. The Main motor could run off the EN bit, and the Lube motor could run off the DN bit.
On the Off delay timer, as soon as the rung goes true, The EN bit goes true as it does for all timers. Since the Off delay timer does not delay the DN bit from shutting off, the DN bit goes high immediately. Remember, the TOF instruction delays the DN bit from shutting off, not turning on. (Plus if we are delaying the DN bit from shutting off, it needs to be high to begin with). While the rung is true, the timer is not timing, and the ACC value is at zero.
When the rung is shut off, the EN bit shuts off immediately. The ACC value will start timing until it reaches PRE then the DN bit will shut off.
Here is what the TOF instruction might look like in logic:
When the motor switch is energized, both the main motor and the lube motor will energize immediately. When the main motor switch is shut off, the main motor shuts off immediately, but since the TOF delays the DN bit from shutting off, the Lube motor will shut off 30 seconds later. Warning: Using the RES instruction on a TOF instruction could cause unpredictable operation.
Types of Timers in PLC | OFF Delay Timer (TOF)
OFF Delay Timer|PLC Timer|Types of Timers in PLC|Types of Timers in PLC | OFF Delay Timer (TOF)|
PLC Ladder PLC Practice Problem PLC Ladder Programming training & tutorials Free Training on PLC Ladder Programming training & tutorials PLC Ladder Logic PLC Timer SCADA Basic PLC Ladder Programming Examples Delta PLC PLC & Visual Basic Communication PLC Definition Introduction PLC Error PLC Error LED RSLinx Tutorial Types of Timers in PLC ladder logic Programming programmable Logic Controllers AB addressing ABB AC Drive AC Drive training cource Actuators Advantages and Disadvantages Addressing of Allen Bradley PLC Micrologix 1000 Addressing of Delta PLC DVP SS/ES/EX Addressing of Mitsubishi PLC FX2N Addressing of Modicon PLC Micro TSX 3722 Addressing of Siemens PLC S7 200 Advantages & Disadvantages of RTD Advantages & Disadvantages of all types Sensors Advantages of SCADA Allen Bradley PLC PWM (Pulse Width Modulation) error codes Allen Bradley SLC Controller Error Codes Ampere Voltage Ratings of circuit brakers Analog addressing Allen bradley Analog input in Allen Bradley PLC Applications of Sensors Capacitive Proximity Sensors blck diagram Capacitive proximity sensors Circuit brakers Circuit diagram of motor starter Communication Between two E1000 HMI and mitsubishi Fx2n PLC Communication between FX3U PLC and SCADA via RS485BD Configuring the DF1 Driver using RSLinx Configuring the Ethernet Driver Connection between 2 E-Terminals and FX2N PLC. DOL Motor Starter PLC logic DOP Series Human Machine Interface DVP14ss Delta HMI Delta HMI Program Download.Delta HMI Communication Cable Delta HMI and RS485 Communication Delta MMI Delta PLC Projects Delta PLC input output addressing Different types of Special motor Diffrence between PLC and DCS Ebook on Basics of Allen Bradley PLC pdf Ebook on Basics of Siemens PLC pdf Ebook on Basics of VFD PDF download Electrical maintenannce tips Electromagnetic relay Error Messages from RSLogix Emulate 500 Failsafe meaning Features of Delta HMI/MMI Following are the Free PLC Software's available from all leading brands such as Allen Bradley Free PLC Ebooks Free PLC SCADA TRAINNING & TUTORIAL Free PLC Training Full form of HART HART OSI reference model HART protocol structure HMI & ZIGBEE How Capacitive Proximity Sensors Works? How Inductive Proximity Sensor Works? How Ultrasonic Sensors Works? How to Select a Suitable Motor How to Select the Right VFD (Inverter) or AC Motor Drive Ladder Logic for AND Ladder Program for Automatic Door open close Ladder Programs for Gates List of Top Most Widely used PLC’s in the Industry List of Widley used PLC Companies. Low cost Wireless I/O’s using PLC Mitsubishi Mitsubishi PLC FX2N & HMI E1000 Networking using BDTP Technology Mitsubishi PLC input output addressing Modbus Communication Modbus Ethernet Modbus Serial Modbus.dll for Visual Basic Mormally open Contact Normally Close Contact Explained Motion Actuators Motor starter in control circuit NAND NO NC Explained NOR Gates with Truth Tables Nashik Nexgenie PLC Features Nexgenie PLC Port Nexgenie PLC input output OFF Delay Timer OLE for Process and Control ON Delay Timer OR Omron On line Ladder Program Editing for RSLogix 500 On line Ladder changes Online Editing Ladder Program Online Servo tuning PID Control Instruction PID PLC PID instruction in Allen Bradley PLC PLC & VB PLC Counter PLC Error Allen Bradley PLC Error messages in Allen Bradley PLC FBD PLC Fault PLC Industrial Automation Training Institute PLC ON Delay Timer PLC Run Led PLC SCADA Communication PLC SCADA DCS Training Centers PLC SCADA Driver PLC SCADA Training Chennai PLC and ZIGBEE PLC application PLC based Automated Guided Vehicle PLC based Final year Project PLC based Line follower robot PLC based Project Report PLC functional Block Diagram PLC input wiring PLC interview Question PLC interview questions PLC maiintence PLC power LED PLC program for star delta starter PLC retentive timer PLC training in Delhi PLC training in Mumbai PLC training in Pune PTO Allen Bradley PTO [Pulse Train Output] Instruction in Allen Bradley PLC Photoelectric Sensor Applications Photoelectric Sensor Applications in Automation industry Power cable Selection Proficy HMI/SCADA Cimplicity 8.1 Programming Languages for PLC Proximity sensor application Push to ON PUSH to OFF PLC program using NO NC and Coil Pwm RSLinx Tutorial | Configuring the DF1 Driver RSLinx Tutorial | Configuring the Ethernet Driver Scaling Analog Input using SCL Instruction in PLC [Scale Data] Schneider Schneider PLC addressing Selction of Servo Motor Selction of Stepper Motor Selection of AC Motor Selection of VFD Selection of stepper or Servo Motor Sensor applications Servo Motor Servo auto tuning Parameters Siemens Siemens input output addressing Signal Cables selection Simatic Wincc SCADA Single Push button to on and off motor Sinking and sourcing operations Softwares used in SCADA Solid State Relay construction Solid State Relay uses and Advantages Sourcing and Sinking Concept in PLC Standard Wiring Color Codes Stepper Motor Applications and Advantages Disadvantages Stepper application Stepper motor Selection Stepper motor and PLC Tag in SCADA Temperature sensors used with PLC Theory of Capacitive Proximity Sensors Theory of Ultrasonic Sensors Theory or Operation of Inductive Proximity Sensors Thermistor & Temp IC Sensors Thermocouple Trial Run of PLC Troubleshooting Allen Bradley PLC with RSLogix Emulate 500 Troubleshooting Tips for Electrical /Electronic Maintenance Tutorial on PLC Types of Actuators Types of Actuators used for Motion in Automation with Advantages & Disadvantages Types of Sensors Types of Timers in PLC | ON Delay Timer (TON) Typical circuit diagram of Star Delta starter Ultrasonic Sensor Applications Ultrasonic sensors Unitronics VB 6.0 and PLC VIsual Basic as SCADA What is HART What is SCADA (Supervisory Control And Data Acquisition) What is SMART Communication What is a PLC ? What is DCS? What is the difference between PLC and Microcontroller? XIO [Examine if Open] & XIC [Examine if Closed] Explained advantages & disadvantages of Servo Motors anlog input addressing DELTA PLC anlog input addressing Mitsubishi PLC anlog input addressing siemens automation training comparison of PLC and DCS connecting field devices to Programmable Logic Controllers contact reting of relay design of fail safe systems digital common ground connections distributed control system drawbacks of Servo Motor fail safe PLC Redundancy modbus examples noise in cables one input one output PLC program using NO NC logic opc overload relay operation photoelectric plc Response Time plc output wiring plc program for TV remote plc training programmable Logic Controllers List relay coil rating relay driving circuit relay isolation voltage selection of relay servo basics servo training star delta starter control wiring diagram types of Counter typical circuit diagram of Direct on line starter